Battery storage can be part of the world’s future energy generation mix to overcome electrical outages caused by severe storms says Lloyd’s Register.
Lloyd’s Register is supporting RES in developing a live 100MW (approx. £40M) storage battery in South Australia. Demand for energy storage is expected to increase after the entire state of South Australia lost power in September. The blackout was a widespread power outage across South Australia that occurred as a result of storm damage to the state’s electricity transmission infrastructure.
Storms can bring devastation to energy supply and getting power back on as safely and quickly as possible for customers is any operator’s priority. RES and Lloyd’s Register – a leading provider of integrity, compliance and specialist risk consulting services – believe that new technology solutions should be planned for now by both government and operators focused on providing future-proof sustainable energy policy and supply.
“Operators are faced with a huge challenge to protect energy generation supply and demand in extreme weather conditions” said Jeremy Moon, Head of Technical at RES in Australia. “We understand this requires investment long term and the adoption of new technology and solutions that enable sustainable energy provision now and in the future. The electrical outages caused by severe storms in South Australia will mean a detailed review of power system security policy focusing on those systems in place now and planned in the future – including newer and flexible systems such as battery storage for security of supply”.
Andrew Jones, Energy Services Manager, at the Australian Power Engineering division of Lloyd’s Register, added that new technology solutions in energy storage can be leveraged to help operators use more cost-effective and locally produced energy, so that when outages do occur both domestic and commercial energy consumers can rely in confidence on new storage systems as a back-up to their power supply.
Lloyd’s Register assessed the faults described in the AEMO preliminary reports through simulations using precise computer modelling of the South Australian system provided by AEMO. The company wanted to see if the system would behave differently if the gas power stations were replaced with inverter-based power stations.
Accurate and detailed inverter models from a leading global OEM were used to provide realistic results. The findings for the system mirrored reports, showing a rapid loading of the interconnection just prior to the South Australian system separation from Victoria. Once the interconnector is heavily loaded, subsequent faults result in large power surges on the interconnector in the lead up to the system collapsing. However, with inverter-based power stations in place, the simulation indicates the generators smoothly resume power after the fault, flows on the interconnection remain stable and the system survives.
As much of the network had been shut down, authorities needed to act carefully to bring it back online and provide a stable network. This was initiated in the first few hours following the start of the outage, initially using the local SRAS provider and the Victorian interconnectors to establish a stable frequency on the network, and then progressively adding South Australian loads and power generators to the network to restore power.
The sudden loss of 445 MW of domestic power would have been a major challenge for any electricity network provider. The subsequent sequence of events resulted in the loss of a further 900MW of imports from Victoria. This study seeks to open discussions on that critical period leading to the loss of the Heywood interconnector and how large scale grid connected battery storage available right now can play a critical role in improving power system events such as those experienced in South Australia
Over the past decade, South Australia has dramatically changed its energy mix. Its coal-fired plants have all been withdrawn and renewable energy now supplies over 40 per cent of its power.
According to Jeremy Moon, it is important to view the study as a power application with time scales of seconds to minutes. The implications are that system resilience can be improved paving the way to greater generation diversity on the current network. Grid operators around the world will almost certainly be reading the reports on the South Australia event, driven by the desire to learn and implement solutions to increase robustness in their own domestic system.